[Date Prev][Date Next][Thread Prev][Thread Next][Date Index][Thread Index]
Re: [APD] Aromat Ballasts Arrived
James H wrote:
> ah, that must be the difference where you live, in canada its now not legal
> to install a pannel that has the ground and neutral bonded, they are
> seperated now but old installs the ground and neutral bar are the same.
> if you hold a continuity meter to the ground and the neutral in your outlet
> it should not show continuity, unless you have the older style pannel where
> they are connected at the panel.
It seems to me that a ground is essentially serving as a "backup"
neutral in the case that something goes wrong with the neutral
grounding. Otherwise, why wouldn't the third prong of outlets just
connect to the neutral since they ultimately lead to the same place?
Am I wrong?
Aquatic-Plants mailing list
Aquatic-Plants at actwin_com